Electricians Northampton MA
Mention Electrical Repairmen and receive a great rate!
Monday 8:00 AM - 6:00 PM
Tuesday 8:00 AM - 6:00 PM
Wednesday 8:00 AM - 6:00 PM
Thursday 8:00 AM - 6:00 PM
Friday 8:00 AM - 6:00 PM
Saturday 8:00 AM - 6:00 PM
Sunday 8:00 AM - 6:00 PM
Circuits & Wiring, Commercial Electrical Services, Electric Safety & Protection, Electrical Inspections, Electricians, Lighting Design & Installation, Residential Electrical Services
Electric Contractors Residential, Electric Heat Elements
Electric Contractors, Fire Alarm Sales & Service
Electric Contractors Residential, Licensed Contractors, Circuit Breakers, Electric Panels & Switchboards, Electric Fuses
Mon-Fri: 07: 00 AM-03: 00 PM
Personal Checks, Cash Only
Electric Contractors Residential, Control Systems & Regulators Dealers
Monday 7:00 AM - 5:00 PM
Tuesday 7:00 AM - 5:00 PM
Wednesday 7:00 AM - 5:00 PM
Thursday 7:00 AM - 5:00 PM
Friday 7:00 AM - 5:00 PM
Saturday 7:00 AM - 5:00 PM
Circuits & Wiring, Commercial Electrical Services, Electric Safety & Protection, Electricians, Residential Electrical Services
Electric Contractors, Builders & Contractors, Electric Equipment Service & Repair
Electric Contractors, Electric Wire & Cable, Phone Equipment & Systems Wiring & Installation
Electric Contractors Residential, Electric Equipment & Supplies Dealers, Electric Equipment & Supplies Job Lots
Electric Contractors Residential, Water Heaters, Fire Alarm Sales & Service
Alarm Systems, Tools
Wiring a 3-way or 4-way switch
Run 2-wire cable from the fixture to the first switch. Between the switches you will need to run 3-wire (with ground) cable. (The white and red wires will be the switched wires.)
In the picture below, we show power coming into the light fixture. The black (hot) wire will pass right through going to the first switch. Attach it to the white wire of the wire running to the switch. The white wire from the power source will attach to the light's white wire. The light's black wire should be attached to the black wire running to the first switch.
At the switch the white wire (hot) coming from the light, will be connected to the dark colored screw. Mark it with a black marker or paint the end black to indicate it is hot. The red and white wire of the 3-wire going to the next switch should be attached to the light colored screws. Connect the black wire of the 3 wire cable to the black coming into the switch from the light.
At the second switch, attach the black wire to the dark screw and the white and red to the light colored screws.